Our Thermography Services can detect problems before they shut down operations or become a danger to plant or employees. The images below show images collected during an evaluation of mechanical, building envelope, and electrical systems.
The above pump motor was found to have overheated bearings due to misalignment. This allowed for corrective procedures to be taken before the pump went down.
The above images show the building was suffering from low thermal resistance at exterior walls due to thermal bridges and an ineffective air barrier, which identified the cause for frozen/split sprinkler lines.
The above images show an overheated three phase and an overheated breaker in a main panelused to spot lose connections or other electrical problems before they become a greater problem, more costly or dangerous.